/ Residual Current Device - Info Please
Any neutral-earth leakage on any circuit will trip a high load on any circuit. For example I had a fault on the loft ring main (caused by compression of the cable), it was neutral - earth. It only tripped when I used the power drill on the downstairs ring.
You can't diagnose these faults very well yourself though. You'll need a sparky but I would give it another night and see how things go.
We had a similar issue that was caused by bits of plaster we'd disturbed getting into a plug socket; not at the time but a few weeks later. Might be worth checking any sockets close to an area you've been working in if so.
With appropriate safety precautions, of course.
The way a RCD/RCBO work is by monitoring the power running through the live also runs through the neutral. If more than 30mA goes into the circuit and it doesn't leave the circuit by the other cable then the circuit has gone down to earth and the RCD/RCBO operates.
what is more likely is that something has got damp and caused the fault or a faulty appliance has caused the RCD to trip.
I'n my opinion it is unlikely that a lamp blowing will cause an RCD to trip. the reason a lamps blowing trips a MCB is because when a current runs through a circuit, the element breaks down and the resistance is lower for a very short amount of time. the resistance dropping increases the current and so the MCB overloads and operates (this is nothing to worry about as most domestic MCB's can withstand a Potentual Fault Current of several 1000 amps)
Hope this helps and isn't to technical for you
GU10 halogen spots are notorious for this.
Washing machine is another likely culprit.
Elsewhere on the site
At a bar in Llanberis an old man chimed in And I thought he was out of his head Being a young man I just laughed it off When... Read more
PowerFingers is a simple, easy to use product which is incredibly effective for Climbers who require finger strength and... Read more